Contains everything you need from the array to the inverter.
Provide your array layout.
We provide pre-cut and terminated PV wire using MC4 connectors to transition into the attic.
Transition through a flashed and sealed pipe boot via RIGID metal.
Sheathe the PV wire inside the attic in 30″ of 1″ MC flex (included) to an attic-mounted rapid shutdown box.
Homerun is made in #8AWG MC Cable.
Come out of attic soffit and transition into EMT.
Field label for NEC 2017 rapid shutdown compliance.
Includes #8 ground.
Up to 250′
Up t three circuits.